1, after opening the box should first check the instructions, factory certificate, packing list is complete. And then check the list of product names, models are consistent, control nameplate is consistent with the order form. If the defect or does not match, should promptly contact with the manufacturers try to solve.
2, when the solenoid valve failure, in order to isolate and facilitate the timely maintenance, it is recommended to install bypass (bypass) device.
3, before installation, please thoroughly purge air bag and pipe, in order to avoid foreign body damage caused by solenoid valve failure.
4, the best way to install the solenoid gas valve is perpendicular to the horizontal pipe, coil up. When the conditions are not allowed, allow ± 30 ° tilt. Otherwise, can not guarantee normal use.
5, in a hazardous environment to prevent the spark may cause an explosion and other accidents, explosion-proof solenoid valve should be used.
6, high-pressure solenoid valve body on the arrow should be consistent with the medium flow.
Usage and charaters:
Application country: Europe, North America
Applicable gas families:LPG/propane/butane
Usage: gas grill, oven, stove